Article 376 (362 in 1999 NEC)
376.23 Wireway Sizing
This section was revised to read:
(A) Bending Radius. Where conductors are bent within a wireway, the wireway must be sized to meet the bending radius requirements contained in 312.6(A) based on one conductor per terminal. For example, a wireway must be sized no less than 6 in. to permit sufficient bending radius for 500 kcmil conductors. Figure 376-1
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.