Receptacle, Cord Connectors, and Attachment Plugs
406.8 Receptacles in Damp or Wet Locations
Parts of this section were revised to read:
(B) Wet Locations
Intent: The revised text to (B)(1) was intended to ensure that all 15 and 20A, 125 and 250V receptacles installed outdoors in a wet location be within an enclosure and cover that is weatherproof at all times, even when an attachment plug is inserted.
(1) 15 and 20A Outdoor Receptacles. 15 and 20A, 125 and 250V receptacles installed outdoors in a wet location must have an enclosure that is weatherproof when the attachment plug is inserted (raintight while-in-use cover). Figure 406-2
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.