Receptacle, Cord Connectors, and Attachment Plugs
406.8 Receptacles in Damp or Wet Locations
Parts of this section were revised to read:
(B) Wet Locations
(2) Other Receptacles. All other receptacles installed in a wet location must comply with (a) or (b):
(a) A receptacle installed in a wet location must have raintight while-in-use cover (enclosure that is weatherproof with the attachment plug cap inserted) if stationary or fixed equipment is plugged into it.
(b) A receptacle installed in a wet location having a weather resistant cover (cover that is weatherproof when the cover is closed and an attachment plug is not inserted) is permitted, if portable equipment is plugged. Figure 406-3
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.