210.4 Multiwire Branch Circuits
Part I. General Provisions
New FPN alerts the Code user to ensure that the continuity of the grounded neutral conductor of a multiwire circuit isnít interrupted (open), because doing so can result in a fire and/or destruction of electrical equipment because of under- or over-voltage.
(C) Line-to-Neutral Loads. Multiwire branch circuits must supply only line-to-neutral loads. Ex 1: A multiwire branch circuit is permitted to supply line-to-line utilization equipment, such as a range or dryer.
Ex 2: A multiwire branch circuit is permitted to supply both line-to-line and line-to-neutral loads if the circuit protection device opens all ungrounded conductors of the multiwire branch circuit simultaneously under a fault condition (multipole circuit breaker with common internal trip). Figure 210-1
FPN: See 300.13(B) for the requirements relating to the continuity of grounded neutral conductor on multiwire circuits.
CAUTION: If the continuity of the grounded neutral conductor of a multiwire circuit is interrupted (open), the resultant over- or undervoltage could cause a fire and/or destruction to electrical equipment. Figure 210-2
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.