Flexible Metal Conduit: Type FMC
348.30 Secured and Supported
Part II. Installation
Revisions to Exception No. 2 relax the requirements for securing flexible metal conduit at terminations where flexibility is required, since there is little point in installing flexible metal conduit at a termination point where flexibility is required, only to have to secure it in place.
New exception permits a€ś6 ft whips for branch circuits without supporta€ť for luminaires or other electrical equipment within an accessible ceiling.
Flexible metal conduit must be installed as a complete system [300.10, 300.12, and 300.18(A)], and it must be securely fastened in place and supported.
(A) Securely Fastened. Flexible metal conduit must be securely fastened by a means approved by the authority having jurisdiction within 1 ft of termination and at intervals not exceeding 41/2 ft. Figure 348-1
Ex 2: At terminals where flexibility is required, unsupported lengths cannot exceed: Figure 348-2
(1) 3 ft for trade sizes 1/2 through 11/4
(2) 4 ft for trade sizes 11/2 through 2
(3) 5 ft for trade size 21/2 and larger
Ex 4: Lengths not exceeding 6 ft can be unsupported from the last point where the raceway is securely fastened for connections within an accessible ceiling to luminaire(s) or other equipment. Figure 348-3
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.