445.18 Disconnecting Means
Change permits a single generator to have multiple disconnecting means to allow flexibility and to provide a safer environment when maintenance is necessary. This rule is necessary because a single generator can be used to supply emergency, legally required, as well as optional standby power through different transfer switches.
Generators must have one or more disconnecting means that disconnects all power, except where: Figure 445-1
Caution: If one generator is used to supply emergency, legally required, as well as optional standby power, then there must be at least two transfer switches. One for emergency power and another for legally required as well as optional stand-by power [700.6(D)].
(1) The driving means for the generator can be readily shut down, and
(2) The generator isnít arranged to operate in parallel with another generator or other source of voltage.
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.