PART III. GROUNDING ELECTRODE SYSTEM AND GROUNDING ELECTRODE CONDUCTOR
250.66 Grounding Electrode ConductoróSize.
Except for a ground rod electrode [250.66(A)], a concrete-encased electrode [250.66(B)], or a ground ring electrode [250.66(C)], the grounding electrode conductor must be sized based on the largest service-entrance conductor or equivalent area for parallel conductors in accordance with Table 250.66
Question: What size grounding electrode conductor is required for a 1,200A service that is supplied with three parallel sets of 600 kcmil conductors per phase? Figure 250Ė116
(A) Ground Rod. Where the grounding electrode conductor is connected to a ground rod, that portion of the grounding electrode conductor that is the sole connection to the ground rod isnít required to be larger than 6 AWG copper. Figure 250Ė117
(a) 1 AWG (b) 1/0 AWG (c) 2/0 AWG (d) 3/0 AWG
Answer: (d) 3/0 AWG
The equivalent area of three parallel 600 kcmil conductors is 1,800 kcmil per phase [Table 250.66].
FPN: Because the grounded neutral service conductor is required to serve as the low-impedance ground-fault current path back to the source, it must be sized no smaller than that shown in Table 250.66 [250.24(C)(1)]. Of course, it must be sized to carry the maximum unbalanced load as calculated by 220.61.
See 250.52(A)(5) for the installation requirements of a ground rod electrode.(B) Concrete-Encased Grounding Electrode (Ufer Ground). Where the grounding electrode conductor is connected to a concrete-encased electrode, that portion of the grounding electrode conductor that is the sole connection to the concrete-encased electrode isnít required to be larger than 4 AWG copper. Figure 250Ė118
See 250.52(A)(3) for the installation requirements of a concrete-encased electrode.(C) Ground Ring. Where the grounding electrode conductor is connected to a ground ring, that portion of the conductor that is the sole connection to the ground ring isnít required to be larger than the conductor used for the ground ring.
A ground ring encircling the building or structure in direct contact with earth must consist of not less than 20 ft of bare copper conductor not smaller than 2 AWG [250.52(A)(4)].
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.