PART III. GROUNDING ELECTRODE SYSTEM AND GROUNDING ELECTRODE CONDUCTOR
250.68 Grounding Electrode Conductor Termination.
(A) Attachment Fitting. The grounding electrode attachment fitting must be accessible.
When the grounding electrode attachment fitting is encased in concrete or buried, it must be listed and identified for this purpose [250.70].Exception 2: An exothermic or irreversible compression connection to fireproofed structural metal isnít required to be accessible.
Exception 1: The grounding electrode attachment fitting to an encased or buried grounding electrode isnít required to be accessible. Figure 250Ė119
(B) Effective Ground-Fault Current Path. To ensure a permanent and effective grounding path for an underground metal water pipe electrode, a bonding jumper must be installed around insulated joints and equipment likely to be disconnected for repairs or replacement. Figure 250Ė120
Continuity of the conductive bonding path for metal water piping as required by 250.104(A) cannot rely on water meters, filtering devices, or similar equipment [250.53(D)(1)].
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.