PART IV. GROUNDING (BONDING) OF ENCLOSURE, RACEWAY, AND SERVICE CABLE
250.86 Other Enclosures.
Metal raceways and enclosures containing electrical conductors that operate at over 50V [250.112(I)] must be grounded (bonded) to an effective ground-fault current path [250.4(A)(5)].
Metal raceways and metal enclosures containing circuit conductors from electrical supply sources that operate at 50V or less aren’t required to be grounded [250.86]. For example, metal boxes used with power-limited fire alarm circuits operating at 50V or less aren’t required to be grounded.Exception 2: Short sections of metal raceways used for the support or physical protection of cables aren’t required to be grounded (bonded) to an effective ground-fault current path. Figure 250–123
NM cable on a wall of an unfinished basement installed, in a listed metal raceway, must be grounded to an effective ground-fault current path [334.15(C)].Exception 3: Metal elbows having 18 in. or more of earth cover aren’t required to be grounded (bonded) to an effective ground-fault current path. Figure 250–124
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.