PART V. BONDING
250.106 Lightning Protection System.
Where a lightning protection system is installed, the lightning protection system must be bonded to the building or structure grounding electrode system. Figure 250–156
The grounding electrode for a lightning protection system cannot be used for the building or structure grounding electrode [250.60].
FPN No. 1: See NFPA 780, Standard for the Installation of Lightning Protection Systems for additional details on grounding and bonding requirements for lightning protection.
FPN No. 2: Metal raceways, enclosures, frames, and other metal parts of electrical equipment may require bonding or spacing from the lightning protection conductors in accordance with NFPA 780, Standard for the Installation of Lightning Protection Systems. Separation from lightning protection conductors is typically 6 ft through air, or 3 ft through dense materials, such as concrete, brick, or wood. Figure 250–158
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.