Air-Conditioning and Refrigerating Equipment
A sentence was added to this section so that it now reads:
Disconnecting means must be located within sight (within 50 ft) from and readily accessible from the air-conditioning or refrigerating equipment. The disconnecting means can be installed on or within the air-conditioning or refrigerating equipment. Figure 440-1
Intent: Problems have been encountered in the field where the disconnecting means was installed on the access panels of A/C and refrigeration equipment. This rule should take care of that problem.
See Article 100 for the definition of “in sight”.
The disconnecting means cannot be located on panels that are designed to allow access to the air-conditioning or refrigeration equipment. Figure 440-2
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.