Swimming Pools, Fountains, And Similar Installations
680.22 Area Lighting, Receptacles, and Equipment
This subsection was revised to read:
Intent: The revised text is intended to clarify that GFCI protection is required for all 15 or 20A, 120V through 240V,240V circuits that supply single-phase receptacles for pool pump motors.
(5) GFCI Protection. All 125V receptacles located within 20 ft. of the inside walls of a pool or fountain must be protected by a ground-fault circuit interrupter. Receptacles supplying pool pump motors rated 15 or 20A, single-phase, 120V through 240V must be provided with GFCI protection. Figure 680-5
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.