Grounding and Bonding
250.8 Termination of Grounding and Bonding Conductors
Revised text clarifies that terminals for grounding conductors or bonding jumpers must be attached to enclosures in a suitable method to ensure an effective ground-fault path.
The termination of equipment grounding and bonding conductors must be by exothermic welding, listed pressure connectors of the set screw or compression type, listed clamps, or other listed fittings. Sheet-metal screws cannot be used to connect grounding (or bonding) conductors or connection devices to enclosures. Figure 250-6
The rule still doesn’t prohibit drywall screws or wood screws for being used for this purpose, just “sheet-metal” screws!
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.