250.2 Definitions Continued
Ground (Earth) . Earth or a conductive body that is connected to earth. Figure 250–6
Grounded . Connected to earth.
Ground Fault . An unintentional connection between an ungrounded conductor and metal parts of enclosures, raceways, or equipment. Figure 250–7
Ground-Fault Current Path [250.2]. An electrically conductive path from a ground fault to the electrical supply source.
The fault-current path of a ground fault is not to the earth! It’s to the electrical supply source, typically the X0 terminal of a transformer.
Grounded (Earthed) . Connected to earth.
FPN: The ground-fault current path could be metal raceways, cable sheaths, electrical equipment, or other electrically conductive materials, such as metallic water or gas piping, steel-framing members, metal ducting, reinforcing steel, or the shields of communications cables. Figure 250–8
The difference between an “effective ground-fault current path” and “ fault-current path” is that the effective ground-fault current path is “intentionally” constructed to provide the low-impedance fault-current path to the electrical supply source for the purpose of clearing the ground fault. A ground-fault current path is simply all of the available conductive paths over which fault current flows on its return to the electrical supply source during a ground fault.
Grounded Neutral Conductor . The conductor that terminates to the terminal that is intentionally grounded to the earth. Figure 250–9
Grounding (Earthing) Conductor . The conductor that connects equipment to the earth via a grounding electrode.
An example would be the conductor used to connect equipment to a supplementary grounding electrode [250.56].
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.