Article 408 (384 in 1999 NEC)
Switchboards and Panelboards
408.21 Grounded Conductor Terminations
A new section was added, which reads:
Each grounded (neutral) conductor must terminate within the panelboard in an individual terminal that is not used for another conductor. Figure 408-2
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.