Swimming Pools, Fountains, And Similar Installations
680.22 Area Lighting, Receptacles, and Equipment
A new item (4) was added and it reads:
Intent: The new rule allows the required 15 or 20A, single-phase, 125V receptacle for outdoor pools and spas for dwelling units [680-22(A)(3)] to be located less than 10 ft., but not closer than 5 ft., from the pool, if the dimensions of the property prevent locating the receptacle 10 ft. away as required in 680.22(A)(3).
(4) Restricted Space. One 15 or 20A, single-phase, 125V receptacle can be installed not less than 5 ft. measured horizontally from the inside wall of the pool at a dwelling unit, if the dimensions of the lot does not allow the receptacle outlet required in 680-22(A)(3) to be 10 ft. from the water. Figure 680-4
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.