700.12 General Requirements
A new subsection was added and it reads:
(B) Generator Set
Intent: The new wording clarifies that a disconnect for the feeder from the generator is not required at or on the building/structure, if the emergency generator disconnecting means is within sight of the building or structure.
(6) Disconnect. Where an outdoor-housed generator for emergency circuits is equipped with a readily accessible disconnecting means located within sight (within 50 ft) of the building or structure supplied, an additional disconnecting means is not required on or at the building or structure for the generator feeder conductors. Figure 700-1
See Article 100 for the definition of “in sight”.
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.