Lighting Systems Operating at 30 Volts or Less
411.4 Locations Not Permitted
Low-voltage lighting systems installed concealed or through a building wall are no longer required to be installed in a Chapter 3 wiring method. Class 2 cables (CL2) are now permitted to be used for this application.
Conductors for lighting systems operating at 30V or less must not be:
(A) Installed in a concealed space or to pass through a building wall, except as permitted in (1) or (2).
(1) Lighting system conductors installed within a Chapter 3 wiring method.
(2) Lighting system conductors supplied by a listed Class 2 power source and installed in accordance with 725.52.
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.