210.8 Ground-Fault Circuit-Interrupter Protection for Personnel
New subsection was added to include kitchens.
(B) Other than Dwelling Units. All 15 and 20A, single-phase, 125V receptacles installed in the locations specified below shall have ground-fault circuit-interrupter protection for personnel.
Intent: The significance of this change is that GFCI protection for personnel is required for all 15 and 20A, single-phase, 125V receptacles installed in kitchens, even those that do not supply the counter top surfaces.
Section 210.8(A)(6) only requires GFCI protection for 15 and 20A, single-phase, 125V receptacles installed to serve counter surfaces for dwelling units, yet 210.8(B)(3) requires all 15 and 20A, single-phase 125V receptacles in kitchens to be GFCI-protected when not in a dwelling unit.
(3) Kitchens Figure 210–3
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.