Circuit and System Grounding
250.32 Buildings or Structures Supplied with Feeder
This subsection added a new requirement and it reads:
(B) Grounded Systems
Intent: The new sentence specifies how to size the grounded (neutral) conductor to a building or structure, when an equipment grounding conductor is not run to the separate building or structure.
(2) Grounded (neutral) Conductor. Where (1) an equipment grounding conductor is not run with the supply to the building or structure, and (2) there are no continuous metallic paths bonded to the grounding system in both buildings or structures involved, and (3) ground-fault protection of equipment has not been installed on the common ac service, the grounded circuit conductor run with the supply to the building or structure shall be connected to the building or structure disconnecting means and to the grounding electrode(s) and shall be used for grounding or bonding of equipment, structures, or frames required to be grounded or bonded.
The size of the grounded conductor shall not be smaller than the larger of:
(1) That required by 220.22 (maximum unbalanced neutral load), or
(2) That required by 250.122 (equipment grounding conductor size). Figure 250–10
When an equipment grounding conductor is not run to a separate building or structure, the grounded (neutral) conductor must be used to provide the effective fault current path required to clear any line-to-case faults in addition to carrying any unbalanced neutral current.
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.