Sensitive Electronic Equipment
A new Article covering the wiring requirements for “Sensitive Electronic Equipment Power or Balanced Power Systems” was added to the 2002 NEC. Balanced power is a separately derived 120V line-to-line, single-phase, 3-wire system with 60V to a grounded neutral conductor on each of two ungrounded conductors. ground from each ungrounded conductor. The purpose of a balanced power system is to reduce objectionable noise in sensitive electronic equipment locations. Its use is restricted to commercial and industrial occupancies that are under close supervision by qualified personnel [647.3]. Figure 647-1
Sensitive Electronic Equipment power systems cannot be installed in dwelling-units.dwelling units.Intent: Balanced power systems have been permitted in the NEC since 1996, however it was located in Article 530 – Motion Picture and Television Studios and Similar Locations. Locations, therefore its use was limited to these applications. By locating the requirements in a separate Article, its use can be greatly expanded, but its use is limited to commercial or industrial occupancies.
This Article contains specific requirements for:
Panelboards -– 647.4(A)
Overcurrent Protection -– 647.4(A)
Junction Boxes -– 647.4(B)
Color Code Conductors -– 647.4(C)
Voltage Drop -– 647.4(D)
Grounding - 647.6
Receptacles (GFCI protected) - – 647.6
Receptacles (GFCI-protected) – 647.7
Lighting - – 647.8
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.