230.70 Service Disconnect - General
New text was added and it reads:
(A) Location of Service Disconnecting Means
Intent: This new rule clarifies that a remote control device such as a shunt-trip pushbutton can be used to control the service disconnecting means, but the disconnecting means must still be located at a readily accessible location either outside the building or structure, or nearest the point of entry of the service conductors in accordance with 230.70(A)(1). Figure 230-3
(3) Remote Control. Where a remote control device is used to actuate the service disconnecting means, the service disconnections means must be located at a readily accessible location in accordance with 230.70(A)(1).
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.