A 120/240V slash circuit breaker cannot be used on the high-leg of a solidly-grounded 120/240V delta system, because the phase-to-ground voltage of the high-leg is 208V, which exceeds the 120 line-to-ground voltage rating.
FPN: Circuit breakers on systems other than on a solidly-grounded wye, particularly on corner-grounded delta systems, should consider the individual pole interrupting capability.
A slash rated breaker cannot be used on corner-grounded systems because phase-to-ground voltage is equal to the phase-to-phase voltage. For more information on this subject, visit www.mikeholt.com/Newsletters/240.85.doc or www.mikeholt.com/Newsletters/240.85.pdf.Intent: The change was the addition of the words “solidly grounded.” This was needed to emphasize that slash-rated devices were not appropriate on resistance-grounded and ungrounded systems.
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.