Optional Standby Systems
702.10 Portable Generator Grounding
A new section was added for grounding portable generators, which reads:
(B) Nonseparately Derived System. If the transfer switch for a portable generator does not switch the grounded (neutral) conductor, then the generator’s equipment grounding conductor must be bonded to the system grounding electrode. Figure 702-3
Intent: The new rule was added to ensure that portable generators are grounded properly so that the system will be safe. Effectively, this rule is only repeating the grounding requirements contained in Article 250.
This means that the grounded (neutral) conductors of the generator must not be bonded to the case [250.142], but this rule requires the case to be bonded to a system grounding electrode, and the grounding electrode system for the building can be used for this purpose.
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.