Grounding and Bonding
250.4 General Requirements for Grounding and Bonding
Change clarifies that swift operation of an overcurrent protection device in the presence of a ground-fault depends upon the existence of an effective ground fault current path from the point of the fault to the power-supply neutral.
The last sentence was revised to make it clear that the earth cannot be used as the effective ground-fault current path. It will not facilitate the opening of the circuit protection device from a ground fault.
(A) Solidly-Grounded Systems.
(5) Effective Ground-Fault Current Path. Electrical raceways, cables, enclosures and equipment, as well as other electrically conductive material that are a€ślikely to become energized,a€ť must be installed in a manner that creates a permanent, low-impedance path that facilitates the operation of the circuit overcurrent device or ground-fault detector for high-impedance grounded systems. Figure 250-3
The effective ground-fault current path must be capable of safely carrying the maximum fault current likely to be imposed on it from any point on the wiring system where a ground fault may occur to the electrical supply source neutral [110.10].
Clearing ground faults (line-to-case faults) is accomplished by bonding all metal parts of electrical equipment and conductive material likely to become energized to the power-supply grounded neutral terminal.
Another factor necessary to help ensure an effective ground-fault current path is that all circuit conductors (ungrounded, grounded and the equipment grounding (bonding) conductor) must be grouped together in the same raceway, cable, or trench [300.3(B), 300.5(I), and 300.20(A)]. Figure 250-4
The earth is not considered an effective ground-fault current path. Figure 250-5
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.