400.5 Ampacity of Flexible Cords
New rule requires conductor ampacity correction when flexible cords are used in an ambient temperature above 86A°F.
Tables 400.5(A) and 400.5(B) list the allowable ampacity for copper conductors in flexible cords with not more than three current-carrying conductors.
Where the ambient temperature exceeds 86A°F, the flexible cord ampacity as listed in Table 400.5(A) or 400.5(B) must be adjusted by using the temperature correction factors listed in Table 310.16. Figure 400-1
Temperature rating for flexible cords are not contained in the NEC, but UL listing standards state that flexible cords are rated for 60A°C unless marked otherwise.
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.