Luminaires (Lighting Fixtures), Lampholders, and Lamps
410.66 Recessed Luminaire Clearances
Part XI. Recessed Luminaires
New requirement address the installation of recessed Non-Type IC luminaires where insulation is required or planned.
(B) Installation. Where the installation of insulation is required or planned, recessed luminaires not identified for contact with insulation must be provided with a field installed means to prevent insulation from being installed above or within 3 in. of the recessed luminaireís enclosure, wiring compartment, or ballast.
This rule places the responsibility for maintaining luminaire-to-insulation clearance on the electrical installer for recessed Non-Type IC luminaires. Since this is beyond the control of the electrical installer where insulation is installed, itís advisable that you use only Type IC rated recessed luminaires.
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.