Luminaires (Lighting Fixtures), Lampholders, and Lamps
Part XIII. Electric-Discharge Lighting (1,000V or Less)
New rule specifies when luminaires with metal halide lamp are to be provided with a method to help contain the arc at end-of-life arc-tube failures.
(F) High-Intensity Discharge Luminaires.
(5) Metal Halide Lamp Containment. Luminaires containing metal halide lamp, other than a thick-glass parabolic reflector lamp (PAR), must be provided with a containment barrier that encloses the lamp or the luminaire must only allow the use of a Type a€śOa€ť lamp. Figure 410-7
Fires have resulted from the spillage of hot arc tube particles from metal halide lamp failures. a€śO-rateda€ť lamps have been designed to meet ANSI containment test for the installation of the metal halide lamp in an open fixture.
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.