Marinas and Boatyards
555.21 Motor Fuel Dispensing Stations — Hazardous (Classified) Locations
Change requires electrical wiring and equipment to be on the opposite side from the liquid piping system of motor fuel dispensers.
Electrical wiring and equipment located at or serving motor fuel dispensing equipment must be in accordance with Article 514, in addition to the requirements of this article. All electrical wiring for fuel dispensing equipment must be installed on the side of the wharf, pier, or dock opposite from the liquid piping system.
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.