Revised text clarifies that Type NM cable used for temporary feeder installations isnít limited by building height, construction type, or concealment.
(B) Feeders. Because of the concern for worker safety, open conductors are not permitted for temporary feeder installations. However, cable assemblies, hard-usage and extra-hard usage cords, and Type NM cable are permitted where the conductors are protected from overcurrent in accordance with their ampacities as required by 240.4. Figure 590-1
Type NM cables can be used in any building or structure, without any height limitation or limitation by building construction type as described in 334.12(2), and without having to be concealed within walls, floors, or ceilings as described in 334.10(3). Figure 590-2
The language in the 2002 NEC prohibited the use of Type NM cable for temporary installations in some building construction types over three floors.
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.