695.4 Continuity of Power
New sentence clarifies that the “carry the locked rotor current indefinitely” requirement only applies to sizing the fire pump circuit protective devices, not the circuit conductors to the fire pump motor.
(B) Supervised Connection.
(1) Overcurrent Device Selection. The overcurrent protective device(s) must be selected or set to carry indefinitely the sum of the locked-rotor current of the fire pump motor(s) and the pressure maintenance pump motor(s) and the full-load current of the associated fire pump accessory equipment when connected to this power supply. The requirement to carry the locked-rotor currents indefinitely does not apply to fire pump motor conductors.
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.