Class 1, Class 2, and Class 3 Remote-Control, Signaling, and Power-Limited Circuits
725.3 Other Articles
Part I. General
Text revised to specify that accessible portions of abandoned Class 2, Class 3, and PLTC cables must be removed.
(B) Spread of Fire or Products of Combustion.
To limit the spread of fire or products of combustion within a building, the accessible portion of optical fiber cable that isn't terminated at equipment and not identified for future use with a tag must be removed. Figure 725-1
This rule doesnít require the removal of cables installed in raceways.
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.