Community Antenna Television (CATV) and Radio Distribution Systems
820.100 Cable Grounding
Part IV. Grounding Methods
New FPN alerts the Code user that limiting the length of the grounding conductor should reduce voltages that may develop between the building’s power and communications systems during a lightning event.
(A) Grounding Conductor.
(4) Length. The grounding conductor must be as short as practicable.
In one- and two-family dwellings, the grounding conductor must not exceed 20 ft. Figure 820-2
FPN: Limiting the length of the grounding conductors will help to reduce voltages between the building’s power and CATV systems during lightning events.
Ex: Where it isn’t practicable to limit the coaxial grounding conductor to 20 ft for one- and two-family dwellings, a separate ground rod not less than 8 ft long [820.100(B)(2)], with fittings suitable for the application [820.100(C)], must be installed. The additional ground rod must be bonded to the power grounding electrode system with a minimum 6 AWG conductor [820.100(D)]. Figure 820-3
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.