695.6 Power Wiring
The text was revised to alert the Code user that the branch circuit conductors for a fire pump motor are sized in accordance with 430.22. In addition, branch circuit conductors must be sized to accommodate the voltage drop requirements of 695.7.
(C) Conductor Size.
Question: What size conductor is required for a 25 hp, 208V three-phase fire pump motor? Figure 695-1
(1) Fire Pump Motors and Other Equipment. Conductors supplying fire pump motors and accessory equipment must be sized no less than 125 percent of the sum of the motor full-load currents as listed in Table 430.248 or 430.250, plus 100 percent of the ampere rating of the fire pumps accessory equipment.
(2) Fire Pump Motors Only. Conductors supplying a single fire pump motor must be sized in accordance with the requirements of 430.22.
This means that the branch circuit conductors to a single fire pump motor must have a an ampere rating of not less than 125 percent of the fire pump motor full-load current (FLC) as listed in Table 430.248 or 430.250.
(a) 4 AWG (b) 3 AWG (c) 2 AWG (d) 1 AWG
Answer: (b) 3 AWG
Conductors sized at 125 percent of the motorís FLC as listed in Table 430.250
FLC of 25 hp = 74.8A, Table 430.250
Conductor = 74.8A x 1.25
Conductor = 93.5A
3 AWG at 75įC is rated 100A
Note: Fire pump motor circuit protective device size must be set to carry indefinitely the sum of the locked-rotor current of the fire pump motor. According to Table 430.151(B), the locked-rotor current of a 25 hp, 208V three-phase motor is 404A.
In addition, branch circuit conductors for a fire pump motor must be sized to accommodate the voltage drop requirements of 695.7.
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.