PART V. BONDING
250.97 Bonding 277V/480V.
Metal raceways or cables, containing 277V or 480V circuits, terminating at ringed knockouts must be bonded to the metal enclosure with a bonding jumper sized in accordance with Table 250.122, based on the rating of the circuit overcurrent protection device [250.102(D)]. Figure 250–139
Exception: A bonding jumper isn’t required where ringed knockouts aren’t encountered, or where the box is listed to provide a permanent and reliable electrical bond. Figure 250–141
• Bonding jumpers for raceways and cables containing 277V or 480V circuits are required at ringed knockout terminations to ensure that the effective ground-fault current path has the capacity to safely conduct the maximum ground-fault current likely to be imposed on it back to the electrical supply source, in accordance with 110.10 and 250.4(A)(5).
• Ringed knockouts aren’t listed to withstand the heat generated by a 277V ground fault because a 277V ground fault generates five times as much heat as a 120V ground fault. Figure 250–140
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.