250.20 Systems Required to be Grounded and Bonded
Alternating-current systems (power supplies) must be grounded and bonded as provided in (A), (B), (C), or (D).
Author’s Comment: System grounding, the intentional bonding of the electrical supply source to the metal case, provides the low-impedance fault-current path necessary to clear a ground fault. Figure 250–43
(A) Alternating-Current Systems Below 50V. Alternating-current systems operating below 50V aren’t required to have the system bonded to the metal case unless: Figure 250–44
(1)The primary is supplied from a 277V or 480V circuit.
(2)The primary is supplied from an ungrounded power supply.
(3)Where installed as overhead conductors outside of buildings.
(B) Alternating-Current Systems Over 50V. Alternating-current systems over 50V that require a grounded neutral conductor must have the grounded neutral terminal [250.26] of the power supply bonded to the system metal parts in accordance with 250.30(A)(1). Such systems include: Figure 250–45
- 2- or 3-wire, single-phase 120V or 120/240V systems
- 4-wire, three-phase wye-connected 120/208V or 277/480V systems
- 4-wire, three-phase delta-connected 120/240V
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.