Swimming Pools, Fountains, And Similar Installations
680.22 Area Lighting, Receptacles, and Equipment
Subsection revised to read:
(C) Switching Devices. Switching devices must be located at least 5 ft. horizontally from the inside walls of a pool unless separated from the pool by a solid fence, wall, or other permanent barrier. Alternatively, a switch that is listed as being acceptable for use within 5 ft. is permitted.Intent: The revised text allows pneumatic switches (i.e. nonelectric) that are listed for this purpose to be within 5 ft. of the water.
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.