Class 1, Class 2, And Class 3 Remote-Control, Signaling, And Power-Limited Circuits
725.6 Mechanical Execution of Work
The text to this section was revised to read:
Class 1, Class 2, and Class 3 circuits must be installed in a neat and workmanlike manner. Cables installed exposed on the surface of ceilings and sidewalls must be supported by the structural components of the building in such a manner that the cable will not be damaged by normal building use. Such cables must be secured to structural components by straps, staples, hangers or similar fittings designed and installed so as not to damage the cable. Figure 725-2
Intent: The revised text clarifies that cables must be properly secured and protected from physical damage.
Cables installed parallel to framing members must be protected against physical damage in accordance with 300.4(D). Figure 725-3
( Click on your connection speed to view )
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.