Receptacles, Cord Connectors, and Attachment Plugs (Caps)
406.8 Receptacles in Damp or Wet Locations
Revised wording clarifies where a receptacle isn't permitted in a bathroom.
(C) Bathtub and Shower Space. Receptacles must not be installed within or directly over a bathtub or shower stall. Figure 406-4
Receptacles must be located no less than 5 ft from any spas or hot tubs [680.21(A)(1) and 680.43(A)(1)].
|If you have already been approved for reprint permission, you may right mouse click on the link above and choose "Save Target As ..." or "Save Link As ..." to save the file to your local computer.
|©2005 Mike Holt Enterprises, Inc.